You are currently reviewing an older revision of this page.
Bentley Hevacomp V8i v26 now includes the option to implement the BS EN 806-3:2006 standards for pipe sizing.
This applies to HWS and CWS systems in both Netsys and System Builder.
Loading units and flow rate calculation methods specified by BS EN 806-3 differ to that of the preceding BS 6700. Both of these standards are available in Hevacomp v8i v26.
The Pipes>Defaults menu now displays options for BS 6700 and BS EN 806-3, as in image below.
If changing the standards on your project, ensure you recalculate your system.
BS EN 806-3 uses both different loading units and a different flow rate calculation method to that of BS 6700.
Should you wish to specify a specific flow rate at your outlet rather than use these loading units, then you can instead enter a figure for Continuous flow, as below.
The effect of the new standards on flow rate results is best shown by example. Consider the following system:
Note that the pipe properties in the example above represent:
Looking at section one, for example, the key figures are:
The Design flow rate can then be obtained from Figure B.1, BS EN 806-3, which plots Total flow rate (x-axis, LU) vs Design flow rate (y-axis, l/s), alongside values for the highest single Loading unit. Below, the total flow rate is highlighted in yellow, and the highest single loading unit is highlighted in red:
The point of intersection between these two lines shows the corresponding Design flow rate on the y-axis, in this case 0.483 l/s.
Product TechNotes and FAQs
Building Product TechNotes And FAQs
Bentley Technical Support KnowledgeBase
Bentley LEARN Server
Bentley's Technical Support Group requests that you please confine any comments you have on this Wiki entry to this "Comments or Corrections?" section. THANK YOU!