Why the spread results are different from stormCAD and Flowmaster .The results are nearly in 6 ft difference though the inputs are same.
The 9.42 discharge is from IN 6-1 and flow from gutter 3 (8.46+0.96).
I have one more question.
Please help me to solve it.
How spread calculation is done in upstream of inlet before flow capture or after?
How did you assign 9.45 cfs. I add it and only became (IN6-1+GU-3=8.46+0.22=8.68)
May be I am missing something.
This is what I see using the model you uploaded.
0.96 cfs from gutter "GU-3":
8.49 cfs from catchment "IN 6-1":
0.96 cfs + 8.49 cfs = 9.45 cfs approaching catch basin "IN6-1" (on the surface):
Bentley Technical Support
Thank you so much it really helped me.I think you missed one question above which was in handwritten that was my biggest doubt.It will be really helpful if you answer that too.
Thank you once again.
Hari, please see my detailed reply in your other thread here: Spread calculation/ Where to assign catchment area if you have both gutter and inlet inside one catchment area
The catchment area that flows onto a certain gutter should be assigned to the next downstream inlet.
Jesse DringoliTechnical Support Manager, OpenFlows ProductsBentley Communities Site AdministratorBentley Systems, Inc.