I have a water model with multiple pressure zones. There is one main low pressure zone that is fed by reservoirs and a couple storage tanks and there are 4 other parasitic higher pressure zones that feed off the low pressure zone. 3 of the 4 pressure zones have their own storage tanks. The 4th pressure zone has just a booster pump that kicks on and off depending on the system pressures seen at the station on the discharge side of the pump. This booster station feeds a couple dead end water mains that go up a steep hill. I am getting a "disconnected demand nodes detected; hydraulic results are likely to be compromised" error when the pump is off which isolates that zone from the low pressure zone which has the water sources. How is a situation like this modeled?
To add to Dr. Walski's reply - the reason you get the "disconnected demands" message is because when you enter a demand in WaterGEMS, the model will always try to satisfy that demand. When that is not physically possible (because the only path supplying them it closed), then you get the message in question and flow will be forced through the pump to satisfy the "known in the equation". If the demands really do get cut off and those customers are without service, you could model this using Pressure Dependent Demands (PDD), where the demand drops as the pressure drops. See more here: Disconnected Demand Nodes user notification when computing model
Jesse DringoliTechnical Support Manager, Haestad ProductsBentley Communities Site AdministratorBentley Systems, Inc.