Hello, I am trying to model a surge relief valve and I need help.
Below is what I have already modeled as an SRV (not SAV). This is to model a residential water supply system where the local pressure gets too high, and a pressure relief valve was installed to reduce the high pressure.
Issue: When I run the simulation, even though the system pressure at the SRV and surrounding nodes (100psi) is greater than the SRV threshold pressure (90 psi), the output graphs do not show any change in system pressure as it increases beyond the threshold pressure. The SRV does not seem to trigger.
What I have already tried:
I have also tried to use the example surge relief file, but again the SRV does not seem to affect the system even when the system pressure goes above the SRV threshold pressure.
I imagine there is something simple that I am missing, I am new to WaterGEMS and there could be something with the scenarios/graphing that I am doing incorrectly.
Please let me know if there is anything else I can do to get the SRV to activate and read out the information on the output graphs.
Surge Relief Valve is an element that should be modeled or analyzed using Hammer.
It appears in WaterGEMS due to Hammer and WaterCAD/GEMS data model integration.
For steady or quasi-steady analysis this element will remain closed.
Juan Carlos Gutierrez Araujo
Juan Carlos Gutiérrez Araújo I.C. M.Sc.
Regional Sale Engineer - Bentley Latin America
Answer Verified By: Kester Wilkening
If you want to model a surge relief valve with WaterGEMS, you would create a branch link to a Pressure Sustaining Valve (PSV) and you would put a reservoir node at the ground elevations just downstream of the PSV. The setting on the PSV should be the pressure or HGL you want to maintain upstream.
This will provide results for steady conditions. If you want to model transients caused by the SRV or determine how the SRV responds to transients, then you need to use HAMMER as Juan Carlos said.
I suggest to you, check valve direction