You are currently reviewing an older revision of this page.
This article explains how to use the Scenario Energy Cost tool in SewerGEMS, SewerCAD, CivilStorm CONNECT Edition (10.00.00.40) or later. The images in this article were taken from SewerGEMS, however the same general workflow applies to SewerCAD and CivilStorm as well.
See this article for information on performing an energy cost analysis in WaterGEMS and WaterCAD.
a. Develop EPS scenario(s) to be used in energy cost.b. Compute the scenario(s).
To do this, go to the Analysis tab and select Energy Costs.
This will open the Scenario Energy Cost manager as shown below.
The scenario to analyze can be selected from the dropdown menu on the top-left side of the Scenario Energy Cost manager.
To convert energy use into energy cost, the applicable energy price tariff must be defined in the Energy Pricing manager.
The Energy Pricing manager can be accessed by clicking the second icon on the top-left of the Scenario Energy Cost manager. It can also be opened by selecting the Pumps tab (or Variable Speed Pump Batteries tab), clicking in an Energy Pricing input field and then selecting the ellipses button "…".
Energy price functions (tariffs) can be created, deleted and renamed using the buttons on the top-left of this dialog. Once an energy pricing plan has been created, the tariff information can be entered on the right pane.
There are two tariff types available.
The bottom part of right pane allows you to enter a description of any peak demand charges if they apply to the study by checking the box labeled "Include Peak Demand Charge?". When this box is checked, the two associated fields become available.
Enter the values for Peak Demand Charge and Billing Period.
Note: You can change the units for the energy pricing by right-clicking on the current units and choose "Units and Formatting". This allows you to change the units and the precision for the data.
Click "Close" to return to the Scenario Energy Costs manager.
Select the Pump tab (or Variable Speed Pump Batteries tab) and select the pumps to include in the energy calculations and the corresponding energy pricing data. When the Energy Pricing input field is selected, a dropdown menu is available to select an energy pricing definition.
To do this, click the first icon on the top-left of the Scenario Energy Cost manager.
Note: The scenario must be computed before computing the energy cost.
Depending on the item you highlight, different results are available. For instance, if you click on the top-most item in the tree, you will see a summary of results that include information on the energy used, the cost, the volume of flow, and the run duration.
Once the energy cost analysis has been computed, the pumps for which the calculation was run will appear in the window on the left side of the dialog.
To view the results for an individual pump, select one of them from the window on the left. A Results table will appear on the right side of the manager.
You can also view the available results fields as a graph by selecting the Graph tab. To select which result field to view, click the pulldown and select the field.
The Pump Usage folder includes this same information, but broken down by the pumps and Variable Speed Pump Batteries that are in the model.
The Pump Time Details and Pumps folders show the combined results such as volume, flow, wire power, energy cost and energy usage for all pumps over time. There is also a graph tab that allows you to view these results in a graphical format.
Peak Energy Demands shows when the peak occurs and the associated costs.
The Results and Graph tabs provide icons to copy and create reports from the data.
Using the Scenario Energy Cost and Energy Management tools in WaterGEMS and WaterCAD
Product TechNotes and FAQs
Haestad Methods Product Tech Notes And FAQs