Administration page used to import sensors data (SCADA sensors or data loggers installed in the system) and sensors characteristics into WaterSight. Sensors types available to upload include the following types: flow, pressure, level, pump power and pump status.
It is possible to import sensors information through a configuration excel file (template file available for download in the Digital Twin Setup page) or to manually add a sensor and its characteristics. After uploading sensor information, it is also possible to edit, delete or copy information, using the available buttons located above the table.
Note: To enable the Copy, Edit and Remove options, please select a sensor first (row in the table). When clicking in a specific sensor (table row) the fields available for editing will appear below the sensor configuration table.
The more actions button includes:
In order to have sensors transmitting real time data into WaterSight, it is required that:
Note: Minimum required fields are marked with an asterisk.
Required field. Unique name in the database for each sensor. Please just consider flow, pressure, level, pump power or pump status types.
Required field. Parameter of the signal in the database/source. Options are flow, level, pressure, power or status.
Required field. Communication or transmit frequency. The typical time interval in minutes in which the collected/read data is sent to the database (eg: 60 = in every 60 minutes data is send to the database).
Note: most SCADA sensors have low communication frequencies (communicate every minute or every 5 minutes for example) but some sensors (like for example dataloggers, AMI systems,, IOT devices) may communicate with the data source only once or twice a day but download data covering multiple time steps at one time
Required field. Minimum read frequency. The time in minutes interval in which at least one data point is expected to be registered in the database (E.G 15 means at least one data point is expected every 15 minutes)
Note: This is different from the communication frequency. One sensor may only communicate once a day, but the registration frequency may be every 5 minutes for example (this means that data gets into the data source only once a day, but when it arrives there is data for all the day in every 5 minutes time step)
The priority when displaying in the sensor overview. Note that a priority of 0 means that the sensor will not be included in the Sensor Overview
Pattern group assigned to the sensor. Pattern groups can be created the the Administration > Settings > Pattern. If Pattern None is selected, then no patterns will be computed and displayed in the sensor graph. Patterns are displayed in the sensors graphs as grey bands.
Tags allow to group sensors inside the application, so it is easier to search and find specific sensors of interest.
Note: When uploading the sensor configuration file for the first time, the default patterns will be assumed:
It is possible to insert tags (or user defined groups) for each sensor, by directly filling the Tags column in the Sensors Configuration Template or by directly clicking Edit in the property grid. Once tags are defined, those will be available in the Network Monitoring pages, so that is easier to search and find specific sensors of interest. Below some examples of groups that may be relevant:
For more information about WaterSight, please go to OpenFlows WaterSight TechNotes and FAQ's.